Since 1968, Service Detectives is your best choice for repair, installation, and service in homes and buildings just like yours in the Southern Illinois. We take special pride in the craftsmen we train and employ--a fact you'll see in their reviews below. Its also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Service Detectives stands behind the work we do as well as comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Electrical, AC, and Furnace Repair in Johnston City, IL. Call us today at (618) 988-8731!
Tony was great found a problem that could have caused a fire. Thank you!
Very happy with the job they did. Will definitely be using them again.
Jason and Matt worked really hard to correct multiple issues to keep us safe and see better efficiency.
Electrician needed to give estimate for complete rewire
Electrician was dispatched to replace weatherhead cap that had blown off during storm
Electrician called out to install a car charging station
Electrician needed to give estimate for complete service upgrade
Electrician needed to fix wiring
Electrician needed to look at Gucci outlet
Electrician needed to do electrical evaluation
Electrician needed to replace GFCIs in kitchen
Electrician need to troubleshot electrical problem
Electrician need to check panel
Electrician needed to diagnose generator not working properly.
Electrician needed to do electrical inspection
Electrician needed to replace pull chain switch on ceiling fan. Installed remote control. Installed energy efficient light bulbs.
Electrician needed to diagnose outside receptacles not working correctly. Also installed outside light with motion detection. Installed disconnect switch for water heater and also installed in use raintight covers on outside ground fault circuit interrupters.
Electrician needed to repair the main electrical panel including installing missing clamps/bushings and repairing oversized breakers. Repaired an open splice. Also replaced the photocell or dusk to dawn sensor on the post light. Installed ground fault circuit interrupters and installed energy efficient L.E.D light bulbs.